dear Manish Joshi ,
Pl refer the following Comments for Electrical panels 
•	Cable Entry from Bottom for both the panels
•	Cable termination from Front side only  
•	LOTO provision for all feeders in Panels (feeder Locking System)
•	Double earthing for All motors 
•	Suitable earth pits should be provide for Earthing
•	RJ 45 Provision for Energy meters (for linking with BMS) in both panels.
•	4P MCCB should be provide in place of 3P MCCB
•	L&T make Motor Protection relay to be provide for Motors having greater than 10HP 
•	Single phase Preventor in circuit for all Motors ( this option normally coming  with MPCB , pl check & Confirm ) 
•	Weather proof / IP-65 Protection to be provide for Control / Operating /Instrumentation panel (because, we are placing this panel inside MEE skid )
•	Color code for panels : Siemens grey 
•	Cable schedule be provide for both power & control cables 
•	20% Spare feeders (or one spare feeder for each HP)  to be provide In MCC Panels 
•	Lamp with switch & 2 single phase sockets with switches to be provide in each panel
•	All Cables should be Aromor with proper dressing & with name plate 
•	All motors to be properly covered with Motor Guards (to protect from rain fall)
•	Load of Each panel In HP & Amp to be provided.

Kindly update the Drawings & SLD with above comments , submit final drawings 

Thanks & Regards 