Dear Sir,

In normal Stripper, MEE and ATFD operation, utility requirement is as follows,

1.	Steam@ 3.5 kg/cm2g for stripper reboiler-1480 kg/hr.
2.	Steam@ 3.5 kg/cm2g for MEE-2950 kg/hr.
3.	Steam@  8 kg/cm2g for ATFD- 850 kg/hr.
4.	Cooling water supply required at 32 deg celcious  inlet temperature at following location
A)	For stripper condenser-108 m3/hr
B)	For MEE condenser-240 m3/hr
C)	For ATFD condenser-81 m3/hr
5.	Cooling water supply pressure required in plant-4 kg/cm2g
6.	Cooling water return pressure required in plant-3 kg/cm2g

