Dear Justin,

The design basis of Pilot Plant is only One trial would be performed at a time.
Therefore the case which we are discussing (PFC + FCE trial) is something which is different than that.

Also to conclude about chiller capacity can you please get the below listed details from chiller supplier:

As Cooling water is replaced with brine for UC210Tw (CB1) chiller as a cooling water utility replacement.

case 1. what would be the cooling load of brine(CB2) with temp +15 deg C, temp difference between supply/return & flowrate of brine if UC210TW (CB1) has a set point of -10 deg C

case 2. what would be the cooling load of brine (CB2) with temp +15 deg C, temp difference between supply/return & flowrate of brine if UC210TW (CB1) has a set point of 0 deg C

case 3. what would be the cooling load of brine (CB2) with temp +5 deg C, temp difference between supply/return & flowrate of brine if UC210TW (CB1) has a set point of -10 deg C