About electrical drawings , I like to inform you that de incoming supply as written in sheet 1 ( drg TF-NARS PD-01),not corresponding whit the supply of Bekaert.
Supply Bekaert is 400 V, 50 Hz,  please make de necessary modifications .
About sheet 2 ( DRG TF-NARS PD-02) , there are now fuses in the supply lines of the pumps , in Belgium is that forbidden, can you modify this whit placing fuses before the contactors from the pump.
