Dear Mr. Prakash
Even in the revised dwg. following points are missing that shuld be  covered & then you can procedd forward 1.After complition as built dwg. is reqyuired 2. Instead of MPCB, SFU with overhead realy is required 3. Panel should be compartmentwise 4. Load manager EM-6400 is required 5. Electrical circut for lighting should be separate 6. Feeder size should be 250 mm X 450 mm.  Rest of the specs are OK , you can process further.