We are received following comments from your side with regards to the electrical drawing submited by us. We get back to you soon on the same.

1.	Vertical cable alley shall be provided for each vertical section.
2.	Cable entry shall be at bottom for all the cables.
3.	Ammeter shall be provided in all the feeder modules and in LPBS as mentioned in data sheets with CT in Y phase. 
4.	Secondary current rating shall be 1A for all the CT.
5.	Voltmeter and energy meter shall be provided after MCCB and R Y B indication shall be provided before MCCB on incomer.
6.	All the SFU shall be rated for 63A with Fuse of 25A.
7.	All the power contactors shall be rated for 16A.
8.	Contactor (16A) shall be provided at the down stream of VFD. VFD bypass contactor shall be provided along with O/L relay as indicated in schematic diagram attached with WO.
9.	One spare SFU out going feeder of 63A shall be provided for meeting the auxiliary power requirement in the plant area.
10.	Control supply shall be tapped for every feeder through separate DP-MCB of 6A rating.
11.	Emergency stop PB not required for main control supply line.
12.	Control ckt for DOL feeders and VFD feeder shall be as per attached drawings. Terminals shall be changed accordingly along with 20% extra terminals.
13.	Facility shall be provided in VFD feeder to extent auxiliary supply of 240V to RPM meter in LPBS.
14.	Agitator speed indication shall be provided in LPBS and in DCS.
15.	Separate MCB shall be provided for cooling fan and interlock shall be provided such that fan shall start only after starting VFD. Louver shall be provided at the bottom of VFD panel for cooling air entry.
16.	Tube light shall be provided in all cable alleys with door limit switch.

M/s Technoforce may also be asked to confirm the following:

1.	Supply of LPBS (Local Push Button Stations) for all the motors. LPBS for pumps shall have Start PB (momentary type), Stop PB (Stay put lockable type) and analogue ammeter with suitable suppressed scale to take care of motor starting current. LPBS for agitator shall have Start PB, Stop PB, Speed increase PB, Speed decrease PB and RPM meter.
2.	Motor for agitator shall be suitable for VFD operation.
