1. TI and TE to be installed in Cooling water inlet and CW inlet and outlet temp should be indicated on panel. PG for inlet and outlet of Cooling water line to provided.
2. 50 NB valve is required at inlet and outlet of condenser i.e. after V-522 and before V-523. This is required for cleaning of condenser after isolation of inlet/outlet valves.
3. Sight glass requried after PU-101
4. FI 101 should give instatanuos and totallised flow on Panel
5. V-512, V-513, V-514, V-515, FI/FT 501 IBR certificate to be provided. FT/FI 501 indication to be given on panel.
6. Below MOC in feed line to be specified.
7. Nomenclature for red and green squares to be provided. We are considering them as a junction.
8. Specification of all equipments in Tecnoforce scope to be provided.
9. MCC, instrruments and electrical specs to be provided for approval. MCC should be non compartmental.