Comments on P&ID:
1. There seems to be typo error in Equipment description of Eq.No.26. Pls. correct.
2. Eq. No. 32: Typo error in capacity. it should be 1000 L.Pls. correct.
3.Pls. mention the sizes of steam condensate lines.
4. We are considering following sizes of lines (RLL scope) which are as follows:
(i) STS-506-65-CS-XX
(ii) STS-501-125-CS-H-XX
(iii) STS-525-50-CS-H-XX
(iv) STS-527-40-CS-H-XX with + reducer 40x150
(v) IA-505-25-GI
(vi) CWS-502-250-CS
(vii) CWR-503-250-CS
5. PSV-502 should be shown after the PRS station i.e. after PT501
6.FT-501 should be shown before moisture separator.
7. Pls. show solenoid valve in steam line with interlockings.