Pl see comments as under :

1.Chilled water requirement : Inlet temp to ATFE/LLE vent Cond /PHE should be -10 deg c and not -5 deg c.

2.Hot water requirement : Inllet temp should be 90 C Max to maintain temp of 50 C inside LLE/Solvent preheater and not 50 C.

Please make corrections and send revised utility sheet.



2.