Layout is uploded. For pannael the distance from MEE is 100 Mts. Based on Existing Pipe Rack the direction of utillity is from south side. Tanks location are positioned in layout. Plan to keep the Heat excahgers & Seperators in first floor ( 2.5 Mt from Ground floor ) and Recirculation pumps on Ground floor so that bottom space under the heat  exchanger is avaliable for service.