Dear Mr. Prakash Following points need to be considered 
1.	I/C is shown as 160A MCCB in GA  & In wiring diagram it is shown as 125 A which is correct  ?
2.	We need to have load manager (  try 6400 ,   ) along with A/M +SS and  V/M +SS & lamp.
3.	Control supply for motor feeder must be separate for each feeder. At least separate MCB is to be considered for each feeder.
4.	Interlocking are not available in manual mode, we required the same.
5.	Auto /manual relay logic is not clear in dwg.
6.	“EXT STOP” is marked to instrument panel, bur they are not shown in instrument panel.
7.	Phase point/fan/light cut of   panel to be separated from control supply MCB.
8.	Indicators & controllers make must of Yokogawa only. Transmitters 4-20 mA o/p is required in all controllers & indicators.
9.	All indicators cum controllers supply must be through individual MCB .
10.	BOM is not available for electrical items & is to be provided.
11.	Electrical switch gear must be of Simens make only.
