Dear Sir, In normal Stripper, MEE and ATFD operation, utility requirement is as follows, 1. Steam@ 4 kg/cm2g for stripper reboiler-990 kg/hr. 2. Steam@ 1.5 kg/cm2g for MEE-1926  kg/hr. 3. Steam@ 8.5 kg/cm2g for ATFD- 590 kg/hr. 4. Cooling water supply required at 32 deg celcious inlet temperature at following location A) For stripper condenser-80 m3/hr(Heat load-400000 Kcal/hr) B) For MEE condenser-162 m3/hr (Heat load-810000Kca/hr) C) For ATFD condenser-54 m3/hr (Heat load-270000 Kcal/hr) 5. Cooling water supply pressure required in plant-4 kg/cm2g 6. Cooling water return pressure required in plant-3 kg/cm2g 