Our reply to your comments:
1.Settling tank tag no. will be corrected.
2.Client to decide the pressure for all the utilities and nitrogen.
3.Nitogen requirement, as specified by you, for decanter will be indicated in the PID.
4.Steam condensate line will be revised to 40NB.
5.We'll add the nitrogen line size.
6.Hot water-supply and return header should be of the same size.
7.Vacuum pump specs uploaded on 25.4.08
8.Client to decide the line sizes for the system which aren't in our scope of supply.
9.GA dwgs of the flash separator and the receivers will be uploaded by 29.4.08
