Dear Sir,
MCC and instrument Panel drawing Rev-1 has been uploaded for your approval.
we taken care of all your concerns on Rev-0 Drawing. Our reply on your points are as follows-1)Incomer feeder will be 400 Amp MCCB TP with RHOM,and for outgoing feeders MPCB with RHOM will be used.
2)Electroinc Energy Meter will be provided in incomer feeder.
3)High Current Switch is a Electronic Microcontroller Based
Protection Relay.Which detects the overload current in the 
motor feeders.it can be programmed as per the motor load/
charactristics.it also has current Disply so that operator
can Monitor it.
4)individual Feeders sizes are Mentioned in the
Revised G.A.DIAGRAM.( rev-1)
5)High current switch is not provided in 75 HP 
 Its a Star/Delta Feeder.

so Please go through Rev-1 Drawing and send your final approval so that we can go ahead for production.